CPU S7-400 Specifications
(Parte 1 de 12)
General Technical Specifications 1
Power Supply Modules 2
Digital Modules 3
Analog Modules 4
Other Signal Modules 5
Interface Modules 6
RS 485 Repeater 7
SIMATIC TOP connect and
SIMATIC TOP connect TPA 8
Parameter Sets for SignalModules A
Diagnostics Data of SignalModules B
Dimension Drawings C
Spare Parts and Accessories forS7-300 Modules D
Guidelines for Handling
Electrostatic Sensitive Devices(ESD)E
List of Abbreviations F
Edition 1/2002 A5E00105505-02
S7-300 Programmable Controller Module Specifications
This manual is part of the documentation package with the order numbers: Programmable Controller S7-300: 6ES7398-8FA10-8BA0
ET 200M Distributed I/O Device: 6ES7153-1AA00-8BA0
The following supplement is part of this documentation:
No. Designation Drawing number Edition 1 Product information A5E00236204-01 08/2003
S7-300 Programmable Controller Module Specifications A5E00105505-02
! Danger indicates that death, severe personal injury or substantial property damage will result if proper precautions are not taken.
indicates that death, severe personal injury or substantial property damage can result if proper precautions are not taken.
! Caution indicates that minor personal injury can result if proper precautions are not taken.
Caution indicates that property damage can result if proper precautions are not taken.
Notice draws your attention to particularly important information on the product, handling the product, or to a particular part of the documentation.
Only qualified personnel should be allowed to install and work on this equipment. Qualified persons are defined as persons who are authorized to commission, to ground and to tag circuits, equipment, and systems in accordance with established safety practices and standards.
Correct Usage Note the following:
This device and its components may only be used for the applications described in the catalog or the technical description, and only in connection with devices or components from other manufacturers which have been approved or recommended by Siemens.
This product can only function correctly and safely if it is transported, stored, set up, and installed correctly, and operated and maintained as recommended.
Trademarks SIMATIC , SIMATIC HMI and SIMATIC NET are registered trademarks of SIEMENS AG.
Third parties using for their own purposes any other names in this document which refer to trademarks might infringe upon the rights of the trademark owners.
This manual contains notices intended to ensure personal safety, as well as to protect the products and connected equipment against damage. These notices are highlighted by the symbols shown below and graded according to severity by the following texts:
We have checked the contents of this manual for agreement with the hardware and software described. Since deviations cannot be precluded entirely, we cannot guarantee full agreement. However, the data in this manual are reviewed regularly and any necessary corrections included in subsequent editions. Suggestions for improvement are welcomed.
Disclaim of LiabilityCopyright Siemens AG 1998–2002 All rights reserved
The reproduction, transmission or use of this document or its contents is not permitted without express written authority. Offenders will be liable for damages. All rights, including rights created by patent grant or registration of a utility model or design, are reserved.
Siemens AG Bereich Automatisierungs- und Antriebstechnik
Geschaeftsgebiet Industrie-AutomatisierungssystemePostfach 4848, D- 90327 Nuernberg
Siemens AG 1998–2002 Technical data subject to change.
Siemens Aktiengesellschaft A5E00105505-02 iiiS7-300 Programmable Controller Module Specifications A5E00105505-02
(Parte 1 de 12)